EdmontonAutomatic power transmission of transformerEmerging style2022-03-27 00:59:31
(I) the distance between the external contour of kV and below dry-type transformer and the surrounding guardrail or courtyard wall shall take into account the convenience of transportation and repair of dry-type transformer, a spacing of more than m shall be reserved; If metal fence is selected, the metal fence shall be grounded and a warning sign shall be hung at a prominent position.Power transformer is one of the key equipment in power station and substation. The function of power transformer is in all aspects. It can not only raise the voltage and send electromagnetic energy to the power consumption area, but also reduce the voltage to each application voltage, so as to meet the needs of power consumption. In short, voltage transformation and blood pressure reduction must be carried out by the transformer.Edmonton,The rate of transformer is: n = P / pxo%, that is, when the copper loss of transformer is equivalent to iron loss, the rate is very large. Therefore, the load of transformer is: = P / PK. Fully consider the active power loss caused by reactive power in the system software during transformer operation. The load adjustment is: it can be seen from the calculation of load formula that the large rate of transformer does not occur when the load is full, Generally, it is about %, we should select effective transformers according to the load condition and load, so as to make the transformer in the situation of economic development and achieve the goal of power saving.When using the oil sample of the power transformer in operation, it is necessary to add some oil from the oil gate valve at the lower part of the oil tank or the sampling gate valve to release about kg of waste liquid stored at the bottom to clean the oil inlet, and then take the oil sample.Bielefeld,When the new oil filled by the power transformer and the oil sample that has just been considered are used, the oil sample can be used only after sufficient standing.The zero line is mainly used in the working circuit. The voltage caused by the zero line is equivalent to the line resistance multiplied by the current of the working circuit. Because of the distance,EdmontonRoutine test of oil immersed transformer, the voltage caused by the zero line can not be ignored. As a countermeasure to maintain life safety, it is more and more unreliable. Ground wire (PE): it is not used as a working circuit, but only as a maintenance line. Use the affirmation of the earth & ldquo; ” Voltage. When the machine and equipment casing is electrified,EdmontonPrice list of power transformer, the current will be quickly grounded. Even if there is a lead for the PE line, it will be grounded from the surrounding grounding body.Oil immersed transformer operation
Fault judgment of power transformerDry type transformer is a common electrical equipment, which can be used to convert the alternating voltage of one standard value into another standard value of the same frequency. The step-up dry-type transformer is used to convert the low-grade alternating voltage into another high-grade alternating voltage of the same frequency. It is widely used in high-frequency industries, such as variable frequency power supply.For the installation of lightning rod it is very easy to damage the relay protection inside and outside of dry-type transformer by lightning. If it is a serious situation, it is very easy to cause fire accidents power failure, damage to machinery and equipment, etc.Potential development,Difference between dry-type transformer and oil immersed transformer:In order to better reduce the probability of short-circuit fault of relay protection dry-type transformer, prevention and key are & ldquo; Prevention and Manipulation & rdquo; Is dominant.There are many connection groups of dry-type transformers, and the selected structures and connections are also different. Then, what are the groups of dry-type transformers? How to carry out the connection? Or basically introduce it with the network of dry-type transformer manufacturers.
The hanging core of dry-type transformer is a vital partsupply,Equipped with a temperature controller, platinum thermistor (pt) is placed beside the embedded hole on the top of the low-voltage solenoid coil to test the winding resistance temperature rise of the transformer, stop the cooling centrifugal fan, set up common problem alarm, overtemperature alarm and overtemperature tripping effect, and provide reliable overvoltage protection machinery and equipment for the dry test transformer, so as to test the safety performance of the transformer operation.The step-up dry-type transformer refers to the instantaneous operation of voltage. At this stage, there are few manufacturers of dry-type transformer that can reasonably guarantee the instantaneous step-up in China. The step-up dry-type transformer has strong step-up capacity and good practical effect. The difference depends on that the transformer power switch without excitation regulator does not have the ability to change gear with load. Because this kind of tap power switch can cut off the whole process in a short time during the whole process of gear change, cutting off the load current will cause arc burning between circuit breakers, tap power on and off or short circuit fault, so the dry-type transformer shall be powered off during regulation. Therefore,If the oil immersed transformer is burned by the cover of the transformer, when the oil immersed transformer fails, open the lower side of the transformer and place an appropriate part. When the oil immersed transformer is on fire, the oil cannot be released to avoid the occurrence of the oil immersed transformer. At the same time, use detection equipment to put out the fire immediately. In order not to expand the hazard, the fire brigade must be notified.When the full load test is carried out and everything is normal, the load can be connected.Loose core screw