Longueuil How much is the installation of small cold storageUse and selection of2022-05-19 00:42:12
The installation of top warehouse plate should be carried out alternately with the installation of wall plate, and the wall plate should leave a gap for withdrawing construction equipment; During the installation of the top warehouse plate, the end steel sheet at the overlap with the wall plate shall be disconnected for mm to prevent the cold bridge from running cold; Two layers of foaming materials shall be evenly and continuously punched on the joint surface between each top warehouse plate. Rivets shall be pulled and fixed at the internal and external lap joints of the steel plate, and the rivet spacing shall be mm; According to the design drawings, if there are supporting beams, columns and supporting steel frames in the warehouse, the setting out and positioning shall be carried out and accurate and clear marks shall be made according to the requirements of the design drawings; Weld or install the support beam, column, support steel frame, etc., and the welded junction shall be moisture-proof and treated according to the drawing requirements.When opening and drilling is required for the top warehouse plate or wall plate, the internal and external setting out and positioning shall be carried out according to the drawing design requirements, and the opening and drilling shall be carried out after review; The inlet hole, liquid inlet hole, and the orifice shall be closed with foaming material or sealant to prevent air leakage and cold running; The door, vent and delivery port shall be decorated with wrapped edges and fixed with pull rivets, with a spacing of mm and mm outside.Longueuil ,Does the unit location meet the relevant conditions? Whether the heat dissipation and pipe length can meet the requirements.Various construction materials,Longueuil Design and installation cold storage installation company, such as material certificate, test report and stage acceptance record, shall be carried out simultaneously with the project construction, timely, accurately and comprehensively reflect the whole process of production and construction, and actively cooperate with the owner in design change and technical negotiation.Puyo,The refrigerator compressor unit generally adopts high-end units with guaranteed quality and strong operation stability. The evaporator adopts the imported joint venture refrigeration air-cooled evaporator, which can effectively meet the refrigeration capacity of the refrigerator and ensure the refrigeration effect of the refrigerator. The refrigerator lamp adopts the special LED energy-saving lamp for the refrigerator, which has the advantages of low temperature resistance, low energy consumption and long service time It can effectively save the operation cost of cold storage.Compression refrigerator is commonly used. It is mainly composed of compressor, condenser, throttle valve and evaporation pipe. The evaporation pipe is installed in the refrigeration warehouse. When the liquid coolant passes through the evaporation pipe, it directly absorbs the heat in the warehouse and cools down.General quick-frozen warehouses are mostly cooled by refrigeration mechanisms, and those with very low gasification temperature are used as coolant to evaporate under low pressure and mechanical conditions, so as to achieve the purpose of cooling and reduction.
The construction of small cold storage is widely used in life, such as food industry, manufacturing industry, etc. since cold storage is so widely used, do you know cold storage? Especially the construction process and steps of cold storage. Understanding the construction process and steps of cold storage is helpful for all links of cold storage maintenance.Nowadays, the application of fresh-keeping storehouse is more and more extensive. It is closely related to our daily life. Fresh-keeping storehouse is mainly to ensure the freshness of food.Cold storage has good water tightness. Polyurethane rigid foam has low water absorption, good permeability to water vapor, disconnected and closed porosity of more than %. It is a dense microporous foam material, which is more dense than air surface, and is not easy to permeate. It belongs to hydrophobic materials.safety requirements ,What should be considered in building a cold storage? In these aspects, food cold storage is a systematic project of artificial refrigeration to ensure food quality and reduce food decay in a low-temperature environment. Refrigeration technology affects the design of food cold storage, meets the needs of refrigeration technology, convenient production, energy saving and cost reduction. What problems should be considered in the construction of food cold storage?Before the acceptance and delivery of the project, the board surface shall be wiped clean. If there is any scratch it shall be treated. There shall be no obvious scratch on the board surface.The combined cold storage does not cool or the cooling effect is poor. Check whether the condenser of the refrigerator is dirty. Whether frost is too thick on the evaporator in the warehouse. Check whether the refrigerant is leaking (apply soapy water to the pipeline connection, and if bubbles are generated it indicates that the refrigerant is leaking). And ask the combined cold storage engineering personnel to supplement the refrigerant and deal with the leakage. Check whether the sealing of the combined cold storage door is intact and eliminate it. Whether the refrigerator of the combined cold storage works. Whether the parameter setting of the computer controller of the cold storage is correct, and reassemble the cold storage door for installation. Check whether the cooler in the cold storage fails and replace it. Whether there is enough clearance for stacking articles in the warehouse and dredge them.
Installation of box and operating device: the design of box shall be reasonable, and the appearance quality shall meet the requirements of beauty and practicality. All buttons, electrical switches, etc. shall be reliable, safe, long-term cold storage installation, cold storage installation, cold storage construction, fruit preservation cold storage, medical cold storage, old brand, price advantage and quality guarantee! Easy to identify and operate. The indicator light shall be simple and clear. The device and each switch shall be installed on the upper side outside the warehouse door, which is easy to operate, read data and not easy to be damaged, and shall be reliably fixed. The device box is installed on the door frame plate on the door opening side. The center line of the box overlaps the center line of the door frame plate. The bottom of the box is mm above the ground and is reliably fixed. The lighting lamp and door frame wire switch in the warehouse are installed directly below the device, and the height of the bottom edge of the switch box is about mm.knowledge,Commissioning cold storage. After all parts of the cold storage are installed and connected, the cold storage can be started for cold storage commissioning. According to the needs of customers, adjust the value of the cold storage, the cold storage can reach the predetermined temperature, the cooling speed and the operation of the cold storage are normal,Longueuil Where is vegetable cold storage installed, as well as some after-sales training.After evacuation, fill the refrigerant into the liquid storage to % of the standard filling volume & mdash; % by weight, then run the compressor and add gas from low pressure to sufficient volume.Installation of refrigeration equipment. The refrigeration system of the cold storage includes evaporator and units outside the cold storage. All equipment shall be installed in accordance with the construction specifications, and corresponding protection measures shall be taken for the installed equipment.Longueuil ,Wall and floor fixtures shall start at corners. According to the plate layout drawing transport the two plates at the corner of the required device to the device location. According to the plate beam height and the model of the angle iron for fixing the mushroom head nylon bolt, drill a hole at the corresponding elevation in the middle of the plate width. When drilling, the electric drill should be perpendicular to the plate surface. Put the mushroom head nylon bolt in the hole, tighten the angle iron, and tighten it horizontally, so as to make the nylon bolt on the surface of the warehouse plate slightly concave. When setting up the wall panels, foam data and other soft data should be laid on the floor slots along with the floor of the storehouse so as to avoid damaging the storehouse. After the two corner panels are neutrally removed from the floor, the plane position of the wallboard and the verticality of the storehouse should be adjusted in time according to the location of the laying line, and check whether the top elevation of the wallboard can be correct. After the position of the wallboard is correct, weld the angle iron on the plate beam and fix the inner and outer corners. When welding the angle iron parts, the angle iron parts of the warehouse plate shall be covered with a shield to avoid the high temperature of the welding ground baking the warehouse plate and welding slag on the warehouse plate during electric arc welding.Quick freezing storehouse is widely used. There are many kinds of temperature in quick freezing storehouse, and multi temperature or double temperature can be realized to meet the needs of different customers. Fault phenomena: unit current is large and voltage is too low; Loose wiring; The unit pressure exceeds the rated pressure; The oil separation core is blocked; Device failure; Host failure; Main motor fault; Fault phenomenon: the unit cannot be started and the fuse is broken; The temperature switch is broken; Loose wiring; Thermal relay of main motor acts; The thermal relay of cold storage fan motor acts; The transformer is broken; No power input (unit); Failure not eliminated (unit); The actuator is faulty.The foaming technology of polyurethane with strong stability makes it have superior bonding performance. The firm combination of polyurethane rigid foam and carrier layer is the basic premise to ensure the stability of external insulation layer. That is, under the unfavorable local temperature and humidity conditions, it can bear various internal and external combined loads such as wind force, self weight and normal collision, and the insulation layer still does not separate and fall off from the carrier layer and remains stable in the state.